RCW/RAW SERIES DOUBLE EFECT ABSORPTION CHILLER This chiller achieves superb energy efficiency at all operating range, from the rated load to. absorption chillers featuring stai .. The absorption chiller is designed in accordance wilh JIS B 5. OYantai Ebara Air Conditioning Equipment Co., Ltd. Chiller-Heater operating time. absorber. Direct Fired Absorption Chiller-Heater ol equipped with latest OYantai Ebara Air Conditioning Equipment Co., Ltd.
|Published (Last):||3 February 2010|
|PDF File Size:||13.62 Mb|
|ePub File Size:||2.83 Mb|
|Price:||Free* [*Free Regsitration Required]|
ABSORPTION CHILLERS & CHILLER/HEATERS
The inner surface of the evaporator cooler tube is washed with water and scrubbed with a bristle brush. To ensure absorptiln performance, we conduct maintenance work in our specialized fields. On-season servicing replaces daily inspection performed by customers with the manufacturer evaluating the operation status.
This work is intended to maintain heat transfer efficiency and to chller contaminants that cause corrosion. Skip To Content Search Site map. The absorbent is sampled and analyzed for chemical composition to determine the inhibitor content and alkalinity. Inspecting safety devices The operation and display of safety devices and thermosensors are inspected.
Welcome To Dunham-Bush
If required to maintain proper characteristics, the solution composition is adjusted by adding the inhibitor or alkalinity adjustment agent. Control panel circuits are inspected.
Test running After the completion of individual inspections, the equipment is test run in the actual operating environment absorptjon check temperatures and pressures of respective parts and to comprehensively check the operation status. Equipment with an intelligent control panel is checked for the proper functioning of each component.
After the completion abskrption individual inspections, the equipment basorption test run in the actual operating environment to check temperatures and pressures of respective parts and to comprehensively check the operation status. This work is intended to maintain the heat transfer efficiency and to remove contaminants that cause corrosion.
The performance of the vacuum pump purge pump is checked. Cleaning the chilled water evaporator tube The inner surface of the evaporator cooler tube is washed with water and scrubbed with a bristle brush.
Also, the operation of electromagnetic contactors, auxiliary relays, and timers is checked. Analyzing the absorbent The absorbent is sampled and analyzed for chemical composition to determine the inhibitor content and alkalinity. A suitable inspection plan designed for your operational needs ensures efficient operation and provides cost reduction.
If required, the equipment is overhauled to restore the pump to optimal performance. Servicing electric components Control panel circuits are inspected.